|LED array available in multiple CCT and CRI combinations with a maximum 3-step MacAdam variation allowance. See Trim Ordering Information for available options. Luminaire input 24VDC from remote-located, 120-240 VAC, high-power-factor power supply (see MRIPS-312, ordered separately). Standard 0-10V dimming with 1-100% range and dim-to-dark capabilities.
|Die-cast aluminum with external radial fins for natural convection.
|All power and signal wiring must be in completely grounded aluminum conduit. Light engine and internal driver are replaceable post-installation. MRI room EMI filters required.
|Luminaire is certified to UL standards by Intertek Testing Laboratory for IC and Wet Location installations. IP64 rating per IEC60598. NSF2 Splash/Non-Food Zone.
|High-Efficiency mixing chamber design with regressed diffused tempered-glass lens producing uniform light output. Round or square aperture. Available with various reflector finishes. See Reflector Finish Ordering Information for available options.
|Photometry tested to the IESNA LM-79-08 standard by an ILAC/ISO17025 accredited laboratory. For photometric information, go to www.kenall.com.
|Die-formed aluminum construction. Vertically adjustable collar accommodates ceiling thicknesses up to 2", adjustable post-installation. Adjustable mounting bars for installation with wood and metal frame joists and T-grid ceiling systems spaced up to 24" on-center. Junction box accessible post-installation from above and below ceiling. (7) 1/2" knockouts.
|IP-rated housing section incorporates the heat sink, LED module, optics and lower trim. Configurable with an IP64-rated Regressed lens trim that is secured to the Rough-In frame with hidden torsion springs. Anti-microbial finish standard on all exposed painted surfaces.
|One-year SafeScan(TM) guarantee on EMI susceptibility. Five (5) year warranty against mechanical defects. Five (5) year warranty on LED lamps and power regulation components for defects resulting in a fixture lumen depreciation of 30% or greater. Warranty is void if all wiring is not shielded in continuously grounded aluminum conduit.