|Doorframe||20-gauge CRS. One-piece 60° beveled perimeter construction. Continuous angle lens retention system. Mechanical guide for doorframe fastener alignment. Doorframe secured to housing with stainless steel aircraft cables and 10 captive flush mounted Phillips head stainless steel fasteners. White TGIC polyester powder coat finish – 5-step pre-treatment. Salt spray test: 1,000 hours; Reflectance: 92%. Doorframe Gasket one-piece closed cell extruded nitrile gasket seals doorframe to ceiling structure.|
|Electrical||Quantity and type as specified – see ordering information. All ballasts UL listed class P. Wireway hole provided with hub/ring assembly. See Ordering Information for alternate or multiple ballasts and optional equipment. Lamps by others.|
|Housing||20-gauge CRS. Hole-free one-piece seam welded construction. White TGIC polyester powder coat finish – 5-step pre-treatment. Salt spray test: 1,000 hours; Reflectance: 92%.|
|Installation||1.0", 1.5" and 2.0" T-Bar installation standard. See Options for T-Bar clips and earthquake clips. Consult factory for custom T-Bar ceilings.|
|Lens||.125" #12 high impact acrylic lens sealed to perimeter ledge of lens aperture with urethane sealant and secured with continuous lens retention system. Lens|
orientation – smooth side out. See Options for alternate lens selections. If required, specify lens overlay combinations inner/outer (Example: R/T).
|Listings||UL and CUL Listed for Wet Location. UL certified IP65 per IEC 60598. Meets K230 Leakage Standard for luminaire leakage in pressurized environments and FED-STD-209E/Class 100 (ISO 5) Cleanrooms. Standard Hazardous Location Listings include Class I, Division 2, Groups A, B, C, D; Class II, Division 2, Groups F, G (and Simultaneous Presence); and Class III. CCEA Approved.|