|Doorframe||18-gauge aluminum. Non-ferrous material content. One-piece inset construction, welded corners. White TGIC polyester powder coat standard – 5-stage|
pre-treatment. Salt spray test: 1,000 hours. Internal hinge design. Twelve (12) captive mounted Phillips-head stainless steel fasteners. Antimicrobial finish optional on all exposed painted components of installed luminaire. Closed cell silicone gasket seals doorframe to housing.
|Electrical||Replaceable high-brightness 6500K LED light array. Luminaire input 24V DC from remote-mounted, 120-240V AC, high power factor power supply (MRIPS-312, ordered separately). Dimming capability controlled through compatible 0-10V dimmer (supplied by others). Dimming range 5-100%. MRI room EMI filter required (supplied by others).|
|Housing||18-gauge aluminum. Non-ferrous material content. Hole-free seam welded construction. White TGIC polyester powder coat standard – 5-stage pre-treatment. Salt spray test: 1,000 hours. Antimicrobial finish optional on all exposed painted components of installed luminaire.|
|Installation||1" or 1.5" T-Bar installation standard. Includes hardware to secure hanger wire. Regress Kit raises fixture 2". All power and signal wiring must be completely shielded in grounded conduit.|
|Lens||Smooth .177" acrylic lens sealed to doorframe with high-strength acrylic adhesive.|
|Listings||Luminaire is certified to UL1598 and UL8750 standards by Intertek Testing Services for Damp Location. NSF2 Splash/Non-Food Zone. Photometry tested to the IESNA LM-79-08 standard by an ILAC / ISO17025 accredited laboratory.|
|Patent||U.S. Patent No. 7,686,484.|
|Regressed Frame Kit (Accessory)||One-piece, .08" thick, seamless aluminum construction TGIC polyester powder coat finish in matte white or black. Provides|
easy-to-install, architectural skylight effect by raising fixture 2-inches above standard 1" or 1.5" T-bar grid ceiling.
|Warranty||One (1) year warranty against defects in materials and workmanship. Five (5) year warranty on LED lamps and driver for defects resulting in a fixture lumen depreciation of 30% or greater. Warranty is void if all wiring is not completely shielded in grounded conduit.|